This guide shows you how to run an SNMP walk in Opsview.
You are here
Monitoring APC UPS - Useful OIDs
If you feel moved to monitor your APC UPS, here are some of the OIDs you'll want to use. These OIDs definitely work with the APC AP9617 management card which plugs in the back of APC devices.
Have a look at all of our hardware monitoring integrations.
UPS Type .22.214.171.124.4.1.3126.96.36.199.188.8.131.52
String containing UPS model, eg: Smart-UPS 1000
Battery capacity .184.108.40.206.4.1.3220.127.116.11.18.104.22.168
Battery capacity as % of total
Battery temperature .22.214.171.124.4.1.3126.96.36.199.188.8.131.52
Battery temperature in Celcius of Farenheit - depending on how UPS is configured
Battery runtime remain .184.108.40.206.4.1.3220.127.116.11.18.104.22.168
Total battery runtime available based on current load.
Battery replace .22.214.171.124.4.1.3126.96.36.199.188.8.131.52
If result = 2 then battery needs replacing (1 = ok)
Input voltage .184.108.40.206.4.1.3220.127.116.11.18.104.22.168
Input voltage, to the UPS device
Input frequency .22.214.171.124.4.1.3126.96.36.199.188.8.131.52
Input frequency in Hz
Reason for last transfer .184.108.40.206.4.1.3220.127.116.11.18.104.22.168
String containing reason for last transfer to battery power
1 No events
2 High line voltage
4 Loss of mains power
5 Small temporary power drop
6 Large temporary power drop
7 Small spike
8 Large spike
9 UPS self test
10 Excessive input voltage fluctuation
Output voltage .22.214.171.124.4.1.3126.96.36.199.188.8.131.52
Output voltage from the UPS
Output frequency .184.108.40.206.4.1.3220.127.116.11.18.104.22.168
Output frequency in Hz
Output load .22.214.171.124.4.1.3126.96.36.199.188.8.131.52
Output load expressed as % of capacity
Output current .184.108.40.206.4.1.3220.127.116.11.18.104.22.168
Output current in Amps
Whether SNMP agent is communicating with UPS device 1 = yes, 2 = no
Last Self Test result .22.214.171.124.4.1.3126.96.36.199.188.8.131.52
Result of last self test as text string. eg: pass or fail.
Last Self Test date .184.108.40.206.4.1.3220.127.116.11.18.104.22.168
Date of last self test
More like this
Kubernetes’ extraordinary resilience tends to change the emphasis of monitoring from alerting to resource and performance management.
This is a brief blog post to explain how I quickly integrated my existing Opsview server with my existing ELK deployment.