A guide on how to monitor Juniper EX switches using SNMP and Opsview.
You are here
Monitoring APC UPS - Useful OIDs
If you feel moved to monitor your APC UPS, here are some of the OIDs you'll want to use. These OIDs definitely work with the APC AP9617 management card which plugs in the back of APC devices.
Have a look at all of our hardware monitoring integrations.
UPS Type .18.104.22.168.4.1.322.214.171.124.126.96.36.199
String containing UPS model, eg: Smart-UPS 1000
Battery capacity .188.8.131.52.4.1.3184.108.40.206.220.127.116.11
Battery capacity as % of total
Battery temperature .18.104.22.168.4.1.322.214.171.124.126.96.36.199
Battery temperature in Celcius of Farenheit - depending on how UPS is configured
Battery runtime remain .188.8.131.52.4.1.3184.108.40.206.220.127.116.11
Total battery runtime available based on current load.
Battery replace .18.104.22.168.4.1.322.214.171.124.126.96.36.199
If result = 2 then battery needs replacing (1 = ok)
Input voltage .188.8.131.52.4.1.3184.108.40.206.220.127.116.11
Input voltage, to the UPS device
Input frequency .18.104.22.168.4.1.322.214.171.124.126.96.36.199
Input frequency in Hz
Reason for last transfer .188.8.131.52.4.1.3184.108.40.206.220.127.116.11
String containing reason for last transfer to battery power
1 No events
2 High line voltage
4 Loss of mains power
5 Small temporary power drop
6 Large temporary power drop
7 Small spike
8 Large spike
9 UPS self test
10 Excessive input voltage fluctuation
Output voltage .18.104.22.168.4.1.322.214.171.124.126.96.36.199
Output voltage from the UPS
Output frequency .188.8.131.52.4.1.3184.108.40.206.220.127.116.11
Output frequency in Hz
Output load .18.104.22.168.4.1.322.214.171.124.126.96.36.199
Output load expressed as % of capacity
Output current .188.8.131.52.4.1.3184.108.40.206.220.127.116.11
Output current in Amps
Whether SNMP agent is communicating with UPS device 1 = yes, 2 = no
Last Self Test result .18.104.22.168.4.1.322.214.171.124.126.96.36.199
Result of last self test as text string. eg: pass or fail.
Last Self Test date .188.8.131.52.4.1.3184.108.40.206.220.127.116.11
Date of last self test
More like this
Looking to reduce packet loss? Read our full guide to find out how.
Despite the lightweight, optimized design of Linux, applications can always introduce anomalies and performance problems can, and will, creep into...