This guide shows you how to run an SNMP walk in Opsview.
You are here
Monitoring APC UPS - Useful OIDs
If you feel moved to monitor your APC UPS, here are some of the OIDs you'll want to use. These OIDs definitely work with the APC AP9617 management card which plugs in the back of APC devices.
UPS Type .220.127.116.11.4.1.318.104.22.168.22.214.171.124
String containing UPS model, eg: Smart-UPS 1000
Battery capacity .126.96.36.199.4.1.3188.8.131.52.184.108.40.206
Battery capacity as % of total
Battery temperature .220.127.116.11.4.1.318.104.22.168.22.214.171.124
Battery temperature in Celcius of Farenheit - depending on how UPS is configured
Battery runtime remain .126.96.36.199.4.1.3188.8.131.52.184.108.40.206
Total battery runtime available based on current load.
Battery replace .220.127.116.11.4.1.318.104.22.168.22.214.171.124
If result = 2 then battery needs replacing (1 = ok)
Input voltage .126.96.36.199.4.1.3188.8.131.52.184.108.40.206
Input voltage, to the UPS device
Input frequency .220.127.116.11.4.1.318.104.22.168.22.214.171.124
Input frequency in Hz
Reason for last transfer .126.96.36.199.4.1.3188.8.131.52.184.108.40.206
String containing reason for last transfer to battery power
1 No events
2 High line voltage
4 Loss of mains power
5 Small temporary power drop
6 Large temporary power drop
7 Small spike
8 Large spike
9 UPS self test
10 Excessive input voltage fluctuation
Output voltage .220.127.116.11.4.1.318.104.22.168.22.214.171.124
Output voltage from the UPS
Output frequency .126.96.36.199.4.1.3188.8.131.52.184.108.40.206
Output frequency in Hz
Output load .220.127.116.11.4.1.318.104.22.168.22.214.171.124
Output load expressed as % of capacity
Output current .126.96.36.199.4.1.3188.8.131.52.184.108.40.206
Output current in Amps
Whether SNMP agent is communicating with UPS device 1 = yes, 2 = no
Last Self Test result .220.127.116.11.4.1.318.104.22.168.22.214.171.124
Result of last self test as text string. eg: pass or fail.
Last Self Test date .126.96.36.199.4.1.3188.8.131.52.184.108.40.206
Date of last self test
More like this
A complete guide on how to set up SNMPv3 traps.
Kubernetes’ extraordinary resilience tends to change the emphasis of monitoring from alerting to resource and performance management.